- 4 Wireless room sensors
- 6 wireless switch actuators
- 1 Wireless repeater
- 1 Gebäude mit 7 Etagen
- 5h Installationszeit
- 20% Energy savings
Energy conservation thanks to weather forecasting and wireless technology
Optimal indoor climate with low energy costs - wishful thinking? Not for IWB CityCenter. Through the weather forecast control of your heating system, the IWB CityCenter saves up to 20% energy annually. Also thanks to the selected wireless system from merkur Funksysteme AG. An overall solution that is not only worthwhile finacially.
Best possible heating comfort, maximum energy efficiency savings. The „integrated energy solutions development“ (IE) division for the IWB CityCenter (customer centre) pursued that vision and was looking for a fitting solution. Because the desired temperature wasn’t always achieved in the rooms of the customer centre: here too warm, there too cold. The result: The potential of energy efficiency in buildings could not be fully exploited.
The solution: Algorithm and radio
Innovative and sophisticated was the IE’s answer to the increasing demand for intelligent energy management. Patrick Wellnitz, Head of development of integrated energy solutions IWB, fell back on two innovative technics:
- New algorithm for intelligent weather forecast based control of heating systems with concrete core activation (TABS)
- Funktechnologie: zur kabellosen Messung der Temperatur und Steuerung der Stellventile
Forecast-based TABS control
Based on local weather forecast data, the controller optimises the operation of heating systems in the IWB CityCenter. The algorithm calculates daily the amount of energy per floor on the basis of forecast data and controls the concrete core activation floor by floor. Here, each floor has a separate control valve.
For regulating the room temperature, the temperature values from several of the IWB CityCenter’s floors were missing. Just three of six floors were equipped with wired temperature sensors. But IWB was not convinced of the fully wired control of the control valves. The effort to pull the data cable from the basement to all floors would have been too great. Furthermore, Patrick Wellnitz is convinced: „The connection of additional temperature sensors would not go smoothly.“ An Ethernet-based solution via WLAN would have been non-transferable for other applications and therefore was out of the question.
The IE division decided to use the radio-based system of merkur Funksysteme AG with controllable wireless switch actuators and wireless sensors. „The solution from merkur Funksysteme AG is simple, reliable and inexpensive. Also in terms of total cost. And thanks to the standardised interface and the exemplary support, it was fast and easily integratable“, says Patrick Wellnitz.
Radio technology convinces
The wireless sensors and wireless switch actuators can be installed easily and neatly thanks to the radio technology. Ideal for fast and reliable data transmission:
- Fast, because the IWB customer centre can measure the temperature values immediately after the implementation of the wireless solution. „Also temperature data from not yet measured floors,“ Patrick Wellnitz confirmed delighted.
- Zuverlässig, weil die funkbasierte Datenübertragung durch den hohen Qualitätsstandard der merkur-Produkte auch in Gebäuden aus massivem Beton einwandfrei funktioniert.